For connecting devices with 0-10 V interface to KNX. With integrated bus coupler and screw terminals (230 V) or plug-in screw terminals (0-10 V). Each individual 230 V switch output can be operated manually with a manual switch.
For installation on DIN rails TH35 according to EN 60715. The bus is connected using a bus connecting terminal; a data rail is not necessary.
KNX software functions: Different dimming curves and dimming speeds, the same dimming time, memory function, ON/OFF delay, staircase time function with/without manual OFF function, scenes (up to eight stored brightness values can be retrieved), central function, logic operation or priority control, blocking function, status feedback, behaviour on bus voltagerecovery.
Switch contact: for switching the electronic ballasts/transformers
Nominal voltage: AC 100-240 V ±10%
Operating voltage: min. AC 90 V – max. AC 265 V
Mains frequency: 50-60 Hz ±10%
Nominal current: 16 A, inductive load cosϕ = 0.6
Incandescent lamps: AC 100 V, max. 1600 W
AC 230 V, max. 3600 W
AC 240 V, max. 3840 W
Halogen lamps: AC 100 V, max. 1086 W
AC 230 V, max. 2500 W
AC 240 V, max. 2608 W
Fluorescent lamps: AC 100 V, max. 1086 VA
AC 230 V, max. 2500 VA
AC 240 V, max. 2608 VA
Capacitive load: AC 100 V, max. 1600 W, 200 μF
AC 230 V, max. 3600 W, 200 μF
AC 240 V, max. 3840 W, 200 μF
0-10 V interface: 0.12-100 mA
Voltage range: DC 0-10 V
Device width: 2.5 HP = approx. 45 mm
Contents: With bus connecting terminal and cable cover.